Send the closed-circuit television camera system down into the pipe to inspect the line. Take measurements for the length of the pipe. Note the pipe's conditions, such as blockages or tree roots.
Remove the CCTV system. Insert the water jet cleaning equipment to clean the pipe of small debris. Connect a root cutter to the water jet nozzle to saw through the invasive roots and wash the pipe clear of the cuttings.
Take the cleaning equipment out of the pipe. Cut the CIPP sleeve to length based on the measurements obtained from the camera inspection. Base the size of the sleeve and thickness of the epoxy resin cure on the size and depth of the pipe.
For example, if you are placing a CIPP lining into an 18-inch pipe, the thickness of applied epoxy resin must be 0.41 inches if the pipe's depth is 14 feet. If the 18-inch pipe is 18-feet deep, you must apply 0.47 inches of resin lining.
Apply the necessary thickness of CIPP epoxy resin to the lining sleeve. Insert the sleeve into the pipe until it is fully extended. Cure the lining against the pipe walls by circulating hot water through the line. Check the water gauges to ensure a constant temperature not exceeding 150 degrees F.
Inspect the edges of the epoxy resin at the edge of the pipe entrance to check for hardness. Pump cold water into the line for the cool-down phase until the temperature is below 100 degrees F.
Drain the water. Feed the CCTV camera into the pipe to inspect for an even curing along the pipe.
Things You Will Need
- Closed-circuit television camera system
- Water jet cleaning equipment
- Remote root cutters
- CIPP sleeve
- CIPP epoxy resin
- Hot water recirculating equipment
- For some applications, the contractor may use air pressure to cure the epoxy resin lining. Have the project properly inspected at every phase of the installation.