Connect the black, white and red wires from the pump to the corresponding terminals on the control box. The control box may have more than three terminals. Refer to the control box wiring diagram to verify the appropriate terminals to use. There are two or three wires that will leave the control box depending on the type of control box.
Run the wires from the control box over to the right side terminals of the pressure switch and secure them. Depending on where the pressure switch is located and the path to get to it, the type of cable used to feed the pump from the main power panel will change. If the path will be dry at all times, then Romex cable will be fine. If there is a possibility of moisture or the cable getting wet, then use underground feeder (UF) cable which is designed for wet conditions.
Strip 1/2 of an inch of insulation from the black and white wires, and connect them to the left side of the pressure switch. If there is a terminal for a ground wire, connect it.
Run the other end of the cable back to the main power panel. Shut off the main breaker and remove the breaker panel cover. Knock out the knockout on the breaker cover corresponding to where the new breaker will go.
Strip 1/2 of an inch of insulation from the black and white wires. Connect the ground wire and the white wire to the common or neutral terminal bar in the power panel. Connect the black wire to the breaker and then plug the breaker into the power panel.
Turn the power back on and test the system.