- Identify the position along the exterior wall where the new electrical service or existing electrical panel is already installed on the opposite interior wall.
- Place the pointed end of the grounding rod 6 inches from the base of the metal shed, in the area of the identified electrical panel. Pound the grounding rod into the earth using the 3 lb. hammer. Leave the top 3 to 4 inches of the 6-foot grounding rod exposed.
- Secure the grounding rod clamp to the exposed top of the grounding rod. Tighten the screws with the screwdriver.
- Insert one end of the #6 AWG bare copper wire into the wire connector of the grounding rod clamp. Run the wire through the opening at least 1 full inch. Tighten the connecting screw.
- Run the other end of the bare copper wire into the electrical panel that houses the circuit breakers or fuses for the electrical system in the metal shed.
- Connect the bare copper wire to the main grounding bus bar inside the electrical panel. The main grounding bus bar will be attached to the rear of the electrical panel. It is the same bus bar in which all the white neutral wires and electrical grounding wires, colored green or bare copper, are connected.
- Cut the #6 AWG bare copper wire to length with the wire pliers. Tighten the #6 AWG bare copper wire into the wire connector that is 3/8 inch in diameter.
- Install the long bonding screw that came with the electrical panel through the main grounding bus bar. The bonding screw will mechanically connect the grounding bus bar to the electrical panel. Follow the electrical panel manufacturer's instructions for proper installation of the panel to the metal building structure.
Things You Will Need
- 6-foot grounding rod
- 3 lb. hammer
- Grounding rod clamp
- Eight feet of #6 AWG bare copper wire
- Wire pliers
- Consult local electrical regulations, as the local governing body may supercede regulations from the NEC.
- Local electrical codes may dictate that all electrical installations are inspected before power can be energized to the new system.
- AWG is the American Wire Gauge standard.